1, can achieve a higher operating temperature (350 ° C) at a lower operating pressure (0.5 MPa), reduce the pressure level of the heat equipment, and improve the security of the system. 2, in the heating uniform, temperature adjustment adopts PID self-tuning intelligent control, temperature control accuracy (1 ° C), can meet the strict requirements of high process standards. 3, small size, less land, can be installed around the heat equipment, no need to set up a special person, reduce equipment investment and operating expenses, and recycle investment. 4, running control and safety monitoring device complete, the temperature rise process is fully automated, simple, easy to install. 6, with low temperature (180 ° C), medium temperature (300 ° C), high temperature type (350 ° C), product specifications, wide selection range. 1, the operator of the heat transfer oil electric heater shall be trained by the heat transfer oil electric heater and the issuance of the local boiler safety monitoring agency. 4, heat-conducting oil electric heater during the temperature rise, the exhaust valve of the expansion tank should be opened to mix steam in a row of air, water and organic heat carriers, and can enter normal operation. 5, the organic heat carrier must be used after dehydration. Different organic heat carriers small space heater should not be mixed. When mixing is required, it should be provided by the organic heat carrier production unit before mixing. 6, the organic heat carrier in use should analyze its residual carbon, acid value, viscosity, and flash point each year. When there are two analyzes or thermal carrier decomposition ingredients, the heat should be replaced. The carrier or the heat carrier is regenerated. 7. The heat-conducting surface of the heat transfer oil should be inspected and cleaned regularly, and the inspection and cleaning should be stored in the boiler technology file. 8, after the heat transfer oil electric heater is installed or significantly repaired, the hydraulic test of 1.5 times the working pressure should be performed by the unit and the installation or repair unit before investing in operation, and can be put into operation after passing. Hydraulic test and airtight test, local boiler safety monitoring agencies should send people to participate.